• Shuffle
Toggle On
Toggle Off
• Alphabetize
Toggle On
Toggle Off
• Front First
Toggle On
Toggle Off
• Both Sides
Toggle On
Toggle Off
Toggle On
Toggle Off
Front

### How to study your flashcards.

Right/Left arrow keys: Navigate between flashcards.right arrow keyleft arrow key

Up/Down arrow keys: Flip the card between the front and back.down keyup key

H key: Show hint (3rd side).h key

A key: Read text to speech.a key

Play button

Play button

Progress

1/12

Click to flip

### 12 Cards in this Set

• Front
• Back
 WHEN SHOULD THE COOLANT PUMP BE OVERHAULED EVERY TWO YEARS WHEN SHOULD THE COOLANT PUMP BE OVERHAULED EVERY TWO YEARS COOLANT CAPACITIES RADIATOR ENGINE BLOCK LINES RADIATOR = 51.8 GAL ENGINE BLOCK = 31.25 LINES = 8.25 TOTAL = 91.3 MAIN COOLANT PUMP TYPE GPM RPM CENTRIFUGAL 411 GPM @ 1800 DESRCIBE MAIN COOLANT FLOW STARTING FROM THE PUMP COOLANT PUMP V OF ENGINE 1ST PATH AFTERCOOLER THERMOSTAT HOUSING SECOND PATH CYLINDER JACKETS CYLINDER LINERS CYLINDER HEADS COOLANT MANIFOLD THERMOSTAT HOUS THERMOSTAT HOUSING TEMPERATURE AND PATH BELOW 170 DEGREE = COOLANT CHANNELED THROUGH BYPASS LINE 170 - 190 DEGREE CHANNELED BOTH TO BYPASS LINE AND RADIATOR OVER 190 DEGREE = CHANNELED THROUGH SEPERATE COOLANT RETURN LINES TO RADIATOR WHAT IS MT3 WHAT IS NORMAL OPERATING TEMPERATURE SENDING UNIT FOR COOLANT TEMPERATURE GAGE 180 - 200 DEGREE F CROSSFLOW HEAT EXCHANGER BTU/MIN RADIATOR PSI TEST RADIATOR PSI MAX RADIATOR CAP PSI 35,800 BTU/MIN 10 PSI TEST 15 PSI MAX 7 PSI CAP PRESSURE IMMERSION HEATER WATT VAC AMP THERMOSTATS SETTINGS 5000 WATTS 208-240 VAC 20.8 AMPS 100 - 120 DEGREE F HOW MANY ISOLATION VALVES ON THE IMMERSION HEATER SYSTEM THREE WHEN SHOULD DCA FILTERS BE CHANGED 250 HOURS OR EVERY 6 MONTHS HOW OFTEN SHOULD THE COOLANT PUMP BE OVERHAULED EVERY 2 YEARS